Automatic control signal, lightning protector, twisted pair wire,
lightning protector, 485 signal lightning arrester.
The signal surge control protector is designed according to the
standard of IEC and GB surge protector. It is suitable for
communication lines, telemetry signals, remote control signals and
other signal devices, so that it is free from induced overvoltage,
operation voltage and electrostatic discharge. The form of
interface is decided by standard screws, and it can protect 1-2
lines. This product adopts modular 35mm guide rail installation
design, which is very convenient for installation and maintenance.
1. using ultra low capacitance design, the signal transmission
characteristic is good.
2. the off state leakage current is extremely low, which does not
affect the normal operation of the
3. energy saving, environmental protection, easy installation,
suitable for all kinds of standard interface types.
Use of attention
1. before the protector is connected to the system, check the
grounding resistance of the grounding grid first, which should meet
the requirements of the specification.
2. connect protector to the front end of the protected device, and
it must be connected reliably.
3. screwdriver loosens the screw on the terminal of the surge
protector. First, the system signal line is connected to the input
end of the surge protector, the output end is received from the
protected equipment end, not the reverse, and the connection part
of the connection terminal is reliable.
|Model and specofocation|| ||TRSS-485|
|Rated Operating Voltage(V)||Un||DC6||DC12||DC24||DC48|
|Max continuous operating voltage(V)||Uc||DC9||DC18||DC36||DC75|
|Voltage protective level(V)||Up〈||〈12||〈30||〈60||〈120|
|Nominal discharge current||In(8/20μS)||5kA|
|Max discharge current||Imax(8/20μS)||10kA|
|Operating condition|| ||Temp:-40℃~+70℃|
| ||Sea level elevation≤3km|
|Remarks|| ||Other max continuous operating voltage can be customized|
Working principle of product
The control signal surge protector is connected to the front end of
the protected equipment. When the transmission line is impacted by
the inductive thunder and other transient overvoltage, the impact
current is discharged to the earth through the protection branch of
the surge protector, and the output voltage is placed in the
allowable voltage range of the equipment, thus ensuring the safety
of the operating equipment.
Zhejiang Thor Electric Co., Ltd is committed to meeting the
requirements of the European Union’s Waste Electrical and
Electronic Equipment (WEEE) directive. This directive requires
producers of electrical and electronic equipment to finance the
take-back for re-use or recycling of their products placed on the
EU market after 2005.